The plant was operating at 100% power when a small fire occorred on the exhaust manifold of an emergency diesel generator that had been started for testing. The fire salf-extinguished when the emergency diesel generator was secured. The emergency diesel generator was not damaged, and there were no personnel injuries. The source of the fire was a small lube oil leak on thge exhaust manifold. The plant remained at power throughout the event.